VERNON MANUFACTURING RECOMMENDS THAT A QUALIFIED TECHNICIAN PERFORM THIS WORK. PLEASE FOLLOW ALL FEDERAL, STATE, AND LOCAL CODES REGARDING ELECTRICAL AND PLUMBING INSTALLATION. USE A DEDICATED CIRCUIT AND SURGE PROTECTION.
If this unit is a Streetside Box, please follow those instructions.
Since each installation is different, mounting hardware is not furnished and the following are general instructions only. Your application will dictate the parameters and hardware needed. We recommend using ½” carriage bolts, washers and nuts for mounting the Flush-mount System to your wall. Some cities mount the plate on the inside, creating a recess. Be sure to allow extra space inside. An awning, or similar cover over the unit, will help keep out moisture and customers dry.
A 21” wide by 21" opening is required. The 24” x 24” aluminum plate has four ½” mounting holes on 22½” centers. Measure and drill the mounting holes in your wall and mount the assembly. Be sure to allow enough room for the Stub Mount Antenna on top of the box.
Install the valve in your water line either horizontal or vertical. Flow direction is marked. Protect it from freezing. A gate valve (not furnished) mounted ahead of the water valve aids in cleaning and repair.
PLEASE NOTE: Valve port #4 must be open to air—DO NOT PLUG THIS HOLE.
At the valve, lengthen the black and red valve wires as needed and bring them in through the 1/2” connector to the terminal strip. Crimp the forked wire ends on and connect them to the #6 and #7 positions on the terminal strip. Refer to the wiring sticker.
Automatic Drain: If so equipped, tie both solenoids in parallel and follow the preceding step. Be sure the green ground wire is tie unde a bolt on the valve.
Card Reader: Download the instruction manual found here to manage your card accounts. If you have problems, call and I will email you this link.
Paperwork is included to set up your account and give customers email receipts. Enter your information and return it to InOne as explained.
Key Switch Override: If so equipped, city personnel can obtain water without having to use money. Simply insert the key and turn. It is labeled “CITY USE ONLY”.
Choice Switch: If so equipped, bring the black wires from the different valves in to the designated positions on the terminal strip. At the valves, tie all red (neutral) wires together and bring only one wire in to position #7. If each valve has an Automatic Drain, follow the instructions above.
NOTE: If your machine is equipped with two timers for different size valves, all wires and positions are tagged.
Except for the valve wires, no other internal wiring is necessary. Refer to all wiring stickers.
To set the timer to deliver the amount of water you want to sell, follow the HRV Timer Settings sheet.
Web: Email: P: 785.536.4412
Mail & Shipping: 712 Maple Gypsum, KS 67448 Proudly manufactured in the USA